48N9 – Horz Supply/Vert Return VAV
Carrier N Series rooftop units are pre-wired and factory-tested in both cooling and heating modes. All 48N models feature a double wall foam panel cabinet design with hinged man-sized access panels.
Units are available in constant volume (CV), staged air volume (SAV), or variable air volume (VAV) applications with a wide variety of gas heating options. Units come with the ComfortLink™ DDC (direct digital control) communicating control system and hermetic scroll compressors on dual independent refrigeration circuits controlled via Electronic Expansion Valves (EXV).
High Capacity and High Efficiency models available, meeting or exceeding EER requirements of AHSRAE Standard 90.1
Multiple high-efficiency scroll compressors include a crankcase heater and spring isolation, providing up to 8 steps of cooling capacity control with intertwined evaporator coils for full-face active operation at part-load conditions
Cooling operating range from 32 to 115F ambient on a standard model, down to -20F with MotorMaster® V control, and upto 125F on high efficiency models
Double wall foam panel construction
Induced draft gas heating system with the direct spark ignition (DSI) control system measures 81% annual fuel utilization efficiency (AFUE) using the integrated gas controller (IGC)
ComfortLink™ control includes: easy to use scrolling marquee display, service diagnostics, run test capabilities, demand limit capability, compressor reverse rotation protection, and BACnet communication option.
California Energy Commission Title 24 Compliant
Dual electrically and mechanically independent refrigerant circuits, with coil frost protection, liquid line filter driers, crankcase heaters, and Electronic Expansion Valves (EXV) standard on all models.
Compressor protection includes high and low pressure transducers with safety cutouts on compressor
Circuit breaker protection for all power components
Cabinet made of pre-painted, galvanized steel with baked enamel finish, which meets ASTM B117 salt spray resistance test
Direct spark ignition, Alumagard Coated Turbo-tubular heat exchangers, and induced draft combination provide for safety and reliability
Reliable Integrated Gas Unit Controller (IGC) provides system evaluation & troubleshooting via on-board LED and two stage gas valves with redundant 100% shutoff
Tested in accordance with UL Standard 1995 and listed by ETL and ETL, Canada
Large hinged service access doors
On-board diagnostics include refrigerant pressure sensors
Auto component testing simplifies troubleshooting
Standard Double wall construction
Shipped with R-410A refrigerant charge
Single point electrical service entry, through unit bottom or side
Standard Limited Warranty
3 years parts only on Novation™ condenser coil
Carrier Weatherexpert – 48N was last modified: March 26th, 2018 by HVAC Expert
People like you shared their purchase and installation experience!
Cozy Comfort Plus Inc. installed a new high efficiency furnace in our house two years ago and it has been operating perfectly ever since. Their service was straight forward, reasonably priced and good value for money. They even walked us through the complicated rebate program that was hard to understand without being involved in the industry.
I would highly recommend them for your next heating and cooling needs.
I requested info online from a few places I found on the internet. Cozy Comfort was the most responsive, not just with the initial info request, but with back-and-forth calls, emails and a site visit. I wanted to convert my wood fireplace to gas, and Brian guided my through the whole process. He explained the type of unit I needed (gas insert), told me the different brands and models that would fit my fireplace opening, and explained the pros and cons of each.
Within a week of my first call, my new gas insert was installed, and a week after that, the stone mantle and hearth were in. The installers laid plastic to protect our flooring, maintained social distance, and were kind to my curious cat and dog. They walked me through how to use the fireplace once the gas insert unit was in. Also, my original fireplace was about 8 inches off-centre (wall is only 13’, so it was noticeable), and Cozy Comfort centred the new one - it looks stunning.
Thanks for everything, Cozy Comfort! I can’t wait for winter 😄